Ques - What is the difference between First Stage and Second Stage Regulator ?
Answer - The Terms First stage and second stage is as per location of installation of regulator. The first-stage gas regulator is responsible for initial pressure reduction and acts as a safety barrier, at primery location it reduce high pressure to medium pressure. while the second-stage gas regulator provides more precise pressure control for specific Appliances. The first-stage regulator adjuss the pressure to medium pressure, whereas the second-stage regulator Precise it (pressure) to meet the requirements of the equipment.
The purpose of the Adjustable LPG Gas Regulator offered at SEPL is to manage the Pressure of gas vapor from the container to the Application Burners. It is rightly said the Adjustable Regulator is the heart of the propane system. The pressure in LPG bullets, Cylinders is 7 Bar at NTP & its increase with increase of atmospheric Temperature max pressure is up to 16.8 Bar. Working Pressure of Commercial & Industrial burners is 0.05 Bar to 0.35 Bar only. To maintain working pressure at burner inlet we need two or three stage regulation of pressure. The adjustable regulator work on first stage as well as on second stage regulation because of their adjusting nature. The adjusting rage of our Adjustable Regulator,2nd Stage Regulator,Second Stage Regulator,Second Stage Gas Regulator is 1psi to 20 psi so this will be used in different pressure ranges. These Regulators are compatible to First Stage as Well as for Second stage Regulation. we can install these regulator on LPG Manifold & also before Comercial Gas Burners where more than 0.5 PSI Pressure is Required.
Our products are the effect of in-depth market examination as well as the progressive designing of our professional manpower. Now, we are added to incorporate innovative and highly creative proficiency to produce and supply a special range of premium quality gas appliances and LPG Adjustable Regulator.
MOC: ZINC/ ALLUMINIUM ALLOY CASTING
MAX INLET PRESSURE: 16.8 KG/SQCM
MAX. OUTLET PRESSURE: 0.5 to 1.2 KG/SQCM
MEDIA: GAS / PNG / LPG